for Acampo, CA
KATHEY - Acampo, CA
Came ready to work. Very good manners.
Courteous and conscientious
JUDY - Acampo, CA
Upon arrival system operational. Cycled heat. No issues. Checked schedule in thermostat. No heat strips installed in equipment to eliminate cool air during defrost cycle. More than likely When unit goes into defrost over night itâ€™s blowing cold air in the home as opposed to heating it. Recommend trying lower heat setting overnight to prevent equipment from coming on.
Replaced defrost control board to allow for proper unit operation. Part is covered under warranty. Cycled heating and cooling. System is operational at this time.
Main unit operational upon arrival. Cycled unit. Unit is operational at this time. Client mentioned the issue happens overnight. Inspected defrost board. Some burning and discoloration on the back of the board. Will check into warranty and availability of defrost control board. Installed new thermostat for addition unit. Tested. Unit operational. Signed up second unit on club membership.
Upon arrival system not operational. No 24v to unit during call for heat. Bypassed thermostat and unit kicked on. Thermostat has failed. Replaced thermostat with Honeywell T6 pro WiFi thermostat. Did not have WiFi T6 on hand. Installed standard T6 for temporary heating. Office will call to schedule return visit to install WiFi tstat. Signed up on club membership for routine maintenance and savings.
Installed new OEM ECM motor Cycled system and it works Checked refrigerant pressures and they are good. Call Complete
**Joined the Guardian Maintenance Program 1yr** Upon arrival system not working properly, no air flow. Went into the attic and diagnosed a Failed ECM motor. No other tests performed due to no air flow. Calling manufacturer tomorrow to get availability on motor. Will call to confirm ordering with homeowner. HVAC non operational at this time.
Performed heat maintenance. Changed filter, heat rise is within specs. Gas pressures are within specs. Flushed drain line. Cleaned flame sensor and burners. Installed IWave, System is operational at this time. Signed back up on superhero club.
Goodman - Removed and properly dispose of existing gas/electric unit, provide and install new 4ton gas/electric up-flow in outdoor closet, install new filter rack with pleated air filter, flushing existing refrigerant/drain lines, connecting to existing refrigerant/drain lines, new a/c pad, disconnect/whip, gas flex connector/shut off valve, sediment gas trap, Honeywell T-6 thermostat, remove existing register to seal boots and re-install existing registers, installation includes, equipment, material, basic, and taxes. Excludes permit. Excludes 10 year labor. GSX140481- 1 Stage Air Conditioner GMES960804CN- 96% 1 Stage Furnace Aspen Coil M# CE48D442100L004 HONEYWELL T6 PRO THERMOSTAT FILTER RACK WITH PLEATED AIR FILTER 14.5 SEER/96% AFUE (AHRI# 201255454) 10 Year Parts/2 Years Labor 10 Year Compressor 10 Year Compressor Lifetime Heat Exchanger 1 Year Sidekick Club (one visit per year)
Performed Sidekick visit. Completed heating and AC inspection and tune up on Bosch heat pump system. Replaced Merv 16 filter with a Merv 13 filter. Bring Merv 16 filter 20x25x5 at next visit. System is operating properly at this time.
Installing new 4ton gas/electric up-flow system on a manufacturing home on 10-7-2020