for Elk Grove, CA
Claudia - Elk Grove, CA
Chris was very respectful and got everything taken care of quickly.
Great checkup, as usual.
JOYCE - Elk Grove, CA
If I ever have an unsatisfactory technician visit, you’ll hear from me for sure.
Impressive Evaluation Detail
Troy - Elk Grove, CA
Very professional & knowledgable
Lisa - Elk Grove, CA
Very thorough estimate appointment-taking time to answer all questions and examine the situation completely
NICKOLAS - Elk Grove, CA
Top notch service and friendly staff every time! No matter when or for what, Huft responds with the beat service. Satisfied customer!
Awesome service, great price
Claudia - Elk Grove, CA
Had a awesome experience with the full process. Trever (installer) and crew were fantastic from start to finish. Respectful of me having an indoor cat to cleaning up when they were finished. Couldn't have asked for a better experience. Also got 3 bids and compared what was going to be done and they had a better price than the other 2.
Great Customer Service
Jennifer - Elk Grove, CA
ARLENE - Elk Grove, CA
Even though couldn't get the toilet first decided on I love the one that they recommended. It works great. The Huff employees did an excellent job plus cleaned up everything when they were finished. Would not hesitate to call on them again for future services.
Huff Home Services
RICH - Elk Grove, CA
We originally purchased our air conditioning unit and heating unit from Brian Huff in 2007. Very good prices, excellent customer service, all technicians are well trained and are completely honest in their evaluation of the annual service for AC and heating. Did I forget how thorough the technicians are. If you are looking for a company which does quality work at reasonable prices consider Huff Home Services. .
On time and very professional.
David - Elk Grove, CA
I couldn't ask for better service. Huft really stays on top of thing and their reps and techs care about the customer and their work.
Quoted new Bosch Variable Capacity Heat Pump System.
Tested and checked all components -Replaced Air Filter 20x24x1, in hallway Return. -No gas leaks -53 degrees temperature rise -Tightened all low and high voltage wiring -Performed safety inspection on Heat Exchanger; No areas of concern. -Evaporator Coil inspected for restricted air, light dust build up -Indoor Blower motor Amps 5.93 out of 14.5A Max -Run Capacitor 33.92uf out of 35uf+-6% -Cleared Inducer port -Cleaned Ignition assembly; Burners & Flame Sensor -Hot Surface Igniter in good shape, no heat stress. -Primary circuit Board okay at this time -Inducer Assembly amp draw .54A out of .68A Max -Inducer Capacitor 4.90uf out of 5uf+-5% HVAC operational at this time. Recommendations New Water Heater 50Gal $2,050 Active Air Purifier $1,062 Call Complete.
Performed sidekick maintenance on 1 year old Lennox gas/electric split system. Everything is within specs on both sides. System is operational and heating and cooling at this time
Performed sidekick visit. Completed heating and AC inspection and tune up on Lennox heat pump system. Replaced filter today. System is operating properly at this time.
Upon arrival talked to customer and came to conclusion that extra work will be needed to be done. Customer decided to modify wood work around gas line instead of modifying gas line.
FaceTime inspection. Inspected system to make sure it is installed correctly and up to code. System is good to go. No corrections needed. Gave customer the packet of inspection paperwork.
Customer request FaceTime inspection service performed FaceTime inspection service inspector states initial inspection is a fail due to no locking caps and carbon monoxide detectors installed carbon monoxide detectors in appropriate areas installed locking caps on condensing unit inspector now state inspection is a pass
Performed a visual inspection of ductwork in the attic and with a camera. Didnâ€™t find any visual sign of a dead rodent. Did notice a strong odor in attic by the front upstairs bedroom. Recommend calling pest control.
Customer request FaceTime inspection service performed inspection service with inspector Chuck Inspector states inspection is a pass
Customer wanted estimate from hybrid water heater with Smud rebate.