for Galt, CA
Very Satisfied with the Service
Carlene - Galt, CA
This company was very easy to deal with. Friendly on the phone and got an appointment for me within three days. The serviceman that came out, Chris, was very professional and thorough. He inspected and tested the H/C systems and discussed all the results with me in a way I could understand. I also liked that there was no high pressure sales for parts or service that I didn’t need. I would highly recommend Huft Heating and Air.
Very good service
DAVE - Galt, CA
Andre from huft was pleasant and really thorough during repair
Teri - Galt, CA
I am unhappy with the quality that Huft provided during the installation and I pointed it out to Chris. He said he would address my concerns and took pictures. If he follows through with that and is able to get my concerns addressed I will be grateful. He was very polite and professional.
Warranty Repair and Duct Inspection
MITSY - Galt, CA
The Huft repairman did a great job of explaining the issues and throughly inspecting things. He also provided photos of the damage and work needed.
Very Good Customer Service
WILLIAM - Galt, CA
Our 8 year old Amana furnace wouldn’t start. Austin our Huft tech found the gas valve wouldn’t open and ordered a new one. After a mix up in parts shipping left us down over a week Austin finally returned with the valve. When he was about to install the new one he found a condensation drain tube was the culprit not allowing the sensor to open the original gas valve. He fixed that and the unit started up. Because of the delay and mix up Austin waved all our repair fees. That seemed to me to be a very honest and upfront compensation for the repair and delays. Thank you, much appreciated
Victoria - Galt, CA
Knowledgeable and friendly. My home is now warm again!
Fast and friendly service
KEN - Galt, CA
Chris was awesome!
Dustin - Galt, CA
Nick - Galt, CA
Extremely fast, friendly and dedicated service
DEBORAH - Galt, CA
Austin was very helpful and polite.
Upon arrival dug around mainline to expose pipe. Found leak from the copper to pvc fitting. Removed old pvc and installed new pvc pipe and with new female adapter and soldered new copper up to new ball valve. Tested by turning water main on. Test well no evident leaks, warranty 1yr parts and labor.
Return to install supply register upon opening of new register found register is incorrect moved living room register two bedroom because living room register is not making noise moved bedroom register to living room where the small noise is going to be less noticed inform customer that if noise persist contact us and I will order to correct vent registers and install them they are 12x6 mounted on a vertical wall see picture
Customer request psychic inspection service performed sidekick inspection service removed inspected and clean flame sensor adjusted gas pressure to 3.5 inches of water column found system is operating properly with a 54Â° temperature rise inspected cooling system checked refrigerant level found refrigerant level is proper at this time found cooling system is operating properly with a 19Â° temperature split
Customer request sidekick inspection service performed sidekick inspection service removed inspected and cleaned flame sensor adjusted gas pressure to 1.9 inches of water column in first stage and 3.5 inches of water column stage to inspected all furnace safeties and connections sound system is operating properly with a 35Â° heat rise Inspected operation of cooling system found system operates properly and cooling with a 26Â° temperature drop Customer states register in master is rattling when system is active verified customers concern remove register and inspected found on two of the damper blades the rivets are loose attempted to compress them was unable to fix the rattling recommend replacing register 12 x 6 Ordered part from thriftyâ€™s on Willcall
Customer go-back work. Found flue pipe to have been taped together. Ran all new flue pipe Resealed and rewrapped both supply plenum/trunk and return trunk Add return air can to provide a transition in supply line Re-insulated lineset Added flashing at supply trunk going into attic Sealed around both supply and return trunk
Upon arrival system not operational. Control board showing error for internal control fault. Reset power to unit. Cycled several times. System is intermittently operational. Operational upon departure. Also noticed thermal stress throughout heat exchanger. Contactor is burnt and pitted. 21 yr old carrier g/e package unit on the roof. R-22 refrigerant. Recommend replacing hvac due to age/reliability, operating condition/cost of repairs, efficiency and r22 phaseout.
Upon arrival system operational. Cycled unit on and off. System operational each time. Client mentioned thermostat was showing â€œin recoveryâ€ on screen. Turned off intelligent recovery mode. Client will see if issue continues.
Replacing all the Ductwork under the house and the one return duct in the attic. Installing manual dampers for air balancing and distribution New floor Registers. New Hi-Flow return grilles for increased air flow. Tape and seal ducts at register connections. Removal and disposal of old ductwork. Installing i-Wave for better air quality.
Upon arrival Water Heater not kicking on Pilot was lit and the code on valve was replace burner. Not the case, reset system and the pilot wouldnâ€™t lite. Tried several times and finally hit the gas valve control and it kicked on. Needs replacement of valve or water heater Call Complete Water heater temporarily working.
Performed heater tune up. Filter recently changed, temp rise is within specs, amp draws are within specs. Cleaned flame sensor and burners, hot surface igniter is reading 187 ohms, adjusted gas pressures to 3.5 inWC. Flushed drain line, tightened and checked all wires, system is operational at this time. Recommend: Upgrade system for efficiency. Maintain maintenance. Surge protector. Hot surface igniter. Primary control board.