for Gold River, CA
Linda - Gold River, CA
Was kept aware of when technician would arrive. Was reassuring to have technician's name ahead of time. Technician (Bradley) was very polite and personable and made quick work of the problem.
Great service and very thorough!!
Chris - Gold River, CA
Chuc was professional, friendly and experienced. His knowledge with HVAC systems was evident.
CLAUDIA - Gold River, CA
Kris was prompt and personable.
FERNANDO - Gold River, CA
Service went very well.
MIKE - Gold River, CA
He was professional and polite
Great visit by Huft, technician very knowledgeable and personable.
Mike - Gold River, CA
Look forward to doing more business with Huft in the future.
CLAUDIA - Gold River, CA
Matt was very knowledgeable and helpful.
Professional and Great Service
CONSTANCE - Gold River, CA
Shun is professional and courteous. He explains things clearly and well. Huft Heating and Air has always given me excellent service and support when I needed to schedule an appt. The customer service representatives have always been polite when scheduling services.
Terry/Roxann - Gold River, CA
Chuc was great! He explained everything he was doing . I didn’t have any additional questions or concerns. Great job!
Nicholas - Gold River, CA
Chuc was very professional
Performed heat tune up on 11 year old amana furnace located in attic. Washed 2 heavily impacted filters. Cleaned all furnace components. Tested all electrical components and tightened connections. Adjusted gas pressure back down to manufactures specs. System is operational and heating at this time. Honored $25 discount coupon. Signed homeowner up for 1year of superhero club membership. Will have 2 more visits after today
Diag preformed on a hp system Upon arrival system is not turning on at all checked air handler found a bad 60amp fuse and also ductwork is falling apart need to be replaced blower motor is leaking oil and blower wheel needs to be cleaned checked system after repair system is operational Client want to talk to a comfort adviser about system replacement with ductwork
Performed after hour diagnostic on a Carrier Heatpump system. Found bad 45 amps fuse at air handler disconnect, replaced 45 amp fuse at no charge per management. Heat strip pulling 16 amps rated for 29 amps, Ecm blower motor pulling at 1.3 amps, all electrical connections are secured. Surge protector, Contactor, Hard Start kit is recommended to prevent future issues. Ran system for 45 mins with no issues at this time.
Gave estimate for water heater provided by homeowner installation.
Replaced hot surface igniter to prevent future breakdowns. Cycled heat. System is operational at this time.
Return to perform quoted repair of installing hard start kit to lower lock rotor amps below manufacture specifications check system before down system is drawing 120 A installed hard start kit and checked operation of system found system is now only pulling 91 Amps system is operating properly Customer was concerned about an error message popping up on the thermostat about the auxiliary heat running for too long verify that refrigerant level is OK verify that condensing unit operates properly verified temperature rise in heat mode down system is operating properly.
Checked and cleaned all components. System is operational at this time. Ductwork is old grey flex and falling apart. Signed up on Super Hero Club membership for routine maintenance and savings.
Customer request heating inspection service performed heating inspection service on heat pump system checked system and feeding mode found system operating properly in heating mode with a 27Â° split checked system in cooling mode refrigerant level is good system is functioning properly in cooling mode with a 20Â° split
Performed diagnostic on a Trane system. Upon arrival found 3 amps fuse blown and tstat wiring at was on incorrect connection. ADT technician approved repair. Replaced fuse and correct wires, system is operational. Emailed a Dale the invoices.
Customer request sidekick inspection service performed sidekick inspection service check systems operation and pressures in heat mode check systems operation in cooling mode checked all systems safeties and connections system is operating properly As per customer request we Will be returning to install hard start kit