for Roseville, CA
Bill - Roseville, CA
He was polite but informed me that they would not install the system I wanted.
Great service. Techs were honest and friendly.
James - Roseville, CA
Sheila - Roseville, CA
Chuc was pleasant & patiently answered my questions.
Debra - Roseville, CA
Very friendly and polite. Explained everything up front. Very happy with his customer service!
Rory - Roseville, CA
Polite, efficient, honest. Excellent experience overall!
BRENT - Roseville, CA
Rory - Roseville, CA
Jet was courteous, efficient, respectful of the condo and had a great attitude 👏🏻👍🏼🇺🇸
ERIC - Roseville, CA
Very knowledgeable and great customer service!
Great service. Would use again.
Susana - Roseville, CA
Wendy - Roseville, CA
Chuc was so great and provided excellent service! Thank you so much!
Remove and properly dispose of existing rooftop package unit. Installation includes equipment, materials, labor, permit, required testing, and taxes.
**Signed up on Superhero club membership today and performed first visit Heating maintenance on a Payne Heatpump package system. Tenant provided incorrect filter sizes, modified filters today for proper fit and quoted tenant for 25x30x1 next filter change out. Model and serial number were unavailable due to sun damage on data plate. Condenser grill was left off due to after market fan motor shaft were too long for grill to be installed. Contactor has pitted marks, compressor capacitor were below spec, blower motor pulling high amps, and Fan motor has oil residue. System is currently operational at this time but should look into new system options due to current conditions of the system and older refrigerant that are phased out.
Performed heater maintenance. Temp rise is within specs, changed filter, amp draws are within specs. Cleaned flame sensor and burners. Gas pressures are within specs. Tightened and checked all wires. Flushed drain line. System is operational at this time.
Completed and emailed options to customer to review and compare with others quotes. Customer not happy that i quoted a 3.ton vs 4.ton like everyone else, upstairs ducting its only 700 CFM.
Gave estimate for kitchen hydro jet and cameradue to customer claims slow draining but only sometimes.
Permit corrections Added grounding wire to junction box on roof Added screws to seismic straps on side of curb to unit Re-painted gas line and condensate line on roof. Customer would like us to schedule re-inspection and, per Matt, provide person to wait for inspector. Customer also expressed concern over temp of certain rooms, says itâ€™s the same issue the previous unit had and that it had cooled those rooms better than before. Just not as good as she had hoped. I donâ€™t recall this attic being very accessible at all.
Performed annual heating inspection and tune up on Lennox split system. System is operating properly at this time. Today is the last visit. Spoke with customer about club memberships.
Performed a diagnostic on a Lennox system. Found bad blower motor and module. Gave homeowner repair vs replacement options. Homeowner will talk it over with his wife over the weekend and will call us on Monday with their decision.
Customer request high flow register be installed in front living room installed new register verified proper operation of register louvers As per customer request documented video and pictures of ductwork in attic also added insulation to supply box While inspecting ductwork in attic found B vent did not have the proper clearance to be able to meet code standards was able to make modifications to achieve a 2 inch clearance in all directions around B vent Went over breakdown of each component purchased with new installed system informed customer that the $207 for return duct installation that was not performed will be refunded and is in the mail currently January 7, 2021. Customer is satisfied with system operation and installation at this time
Permit corrections. Re-routed and strapped flue to ensure 1â€ clearance at rafter. Added straps. Strapped up supply plenum on both sides. Sealed collar on back side of plenum that had not been sealed. Strapped lineset back from furnace toward outside. Re-routed gas line and trap and flex to create clearance in front of furnace. Cut access in platform to leak check gas line fittings under platform, capped those off. Altered return air grill anchors to allow installation of new filter. Sealed all â€˜holesâ€™ found on top of furnace.