for Lincoln, CA
Phong was Great
Adam - Lincoln, CA
Huft is a great company. I started using them based upon a recommendation from a friend, and I have not regretted it. The technicians are always pleasant, explain what they are going to do, and what they did, and always provide options for any service necessary. Great company and great employees.
Great service and very professional.
Charles - Lincoln, CA
I trust this company to be honest and they are always on time. The service tec spent an hour and a half at my house but could not fix my 50 year old wall heater but he did not charge me a service fee. Good customer service.
Great service, awesome
Nick - Lincoln, CA
He was awesome, very informative and just all around great person!
Brian - Lincoln, CA
Shun was very knowledgeable, great job in communication.
Not very happy with communication
Shana - Lincoln, CA
Chad - Lincoln, CA
Adam - Lincoln, CA
The technician that came to my house was great. Virtuous and didn’t push any sales on me. I was referred by RAD radio and I can see why HUFT partners with RAD. Excellent job!
TORI - Lincoln, CA
Matt from Huft has been to our house twice now and both times was great - experienced, professional, on time. Nothing bad to say. The Huft quote is better priced than most we have had, backed by their guarantees.
Susan - Lincoln, CA
Efficient and personable. Answered all my questions in a way I could understand.
Wayne - Lincoln, CA
Chuc figured out the part he was sent to replace wasn’t the cause of the issue, he got the heat working before the root cause could be remedied.
Gave options on Lennox and Rheem 2 stage equipment for zoning.
Performed last visit Heating maintenance on a Goodman furnace. Found high gas pressure at 3.8, adjusted back to spec at 3.5. Gas line are inspected to ensure no leak, cleaned and resurfaced flame rod, wiped down and vacuumed blower compartment, all electrical components were within spec and system is operating properly. System was without flood safety switch and surge protection, recommend installing to prevent future issues. Courtesy replacement thermostat batteries. Continuing on Superhero club membership today and will have two more visits left.
Homeowner wanted to replace the gas shut off valve and flex line on his wall furnace. In the process to turning off the main gas line at the meter the shut off valve broke. Homeowner will call pg&e to have it fixed. He will be calling us back in the near future to install a complete system instead. N/C for todayâ€™s visit since we couldnâ€™t do the repair per MB.
3 Ton 16ACX & ML296 Horizontal Replace existing split system with a Lennox High Efficiency Two Stage split system. Install NEST Learning Wi Fi touchscreen thermostat. Add an additional 10â€ R-8 Silver-Jacketed return air and a 14â€ X 14â€ High Flow grill in the Master Bath area. Install the Quiet Cool Trident Pro 3.3 Whole House Fan. Installation includes: All Huft Comfort Guarantees, installation by HUFT Journeyman employees, new condensate drain pan with overflow safety switch, Title 24 HERS certification with a third party including duct leakage test, gas flex with ball type shut off valve, electrical disconnect with properly sized fuses, perform line set flush, dispose of existing equipment, weather tight flexible whip at condenser, new PVC flue pipe system, new high flow return air grill, Healthy Climate 13 filter, seal register boots to ceiling and install new registers, labor, material, taxes, permits and rebate processing. Lennox: 16ACX-036-230, ML296UH070XV36B, LC23
Performed a heat tuneup on a York furnace. Checked heat operations, all components, and safeties. Found hot surface igniter reading high resistance at 94.7 ohms. Homeowner wants to hold off on replacing it today. System operations ok at this time.
Upon arrival defective fill up valve continued to over fill toilet tank. Replaced fill up valve. Flushed toilet 3 times to test for leaks. Test well no evident leaks.
Customer request heating inspection service performed heating inspection service remove inspected and clean flame sensor adjusted gas pressure to 3.5 inches of water column system is operating properly
Originally $795, Gave 5% Veterans discount. Installed OEM circuit board Cycled system and furnace ignited and is now heating. HVAC is operational System is very dirty **Highly recommend tune ups for HVAC**
Performed diagnostic with zone issue, found one room upstairs connected to downstairs zone and one room downstairs connected to upstairs zone, need installer to return and switch zone ducts.
Need to call tomorrow for confirm price and Availability on the primary circuit board. Upon arrival main concern was the Furnace doesnâ€™t cycle on. Went on the roof and opened up the system to check the system out. Diagnosed failed primary circuit board. Not sending voltage for spark ignition. Call not complete, needs to follow up